Water Quality Notice: WATER QUALITY CHANGES December 27, 2018 and January 8, 2019
WATER WILL CONTINUE TO MEET ALL REGULATORY STANDARDS
We are notifying you in advance of expected changes in drinking water quality from the San Francisco Public Utilities Commission (SFPUC) on December 27, 2018 and January 8, 2019. The SFPUC system will begin reducing flows from the Hetch Hetchy source December 27th, progressing to a full Hetch Hetchy shutdown on January 8th. The Hetch Hetchy shutdown will last until March 12th. During this shutdown, local sources from the Sunol Valley Water Treatment Plant (SVWTP) will supply the regional system with water. A follow up notification will distributed in March when the Hetch Hetchy supply is restored. The changes below will likely affect Stanford approximately 24 hours after the date noted below (average travel time from East Bay facilities to Stanford).
EXPECTED WATER QUALITY:
||SFPUC as of 12/19/2018
||SFPUC as of 12/27/2018
||SFPUC as of 1/8/2019
Blend (Hetch Hetchy)
Blend (SVWTP and Hetch Hetchy)
Blend (SVWTP )
|Chlorine residual (total)||mg/L||3.1||3.0||3.0|
WHAT DOES THE WATER QUALITY CHANGE MEAN FOR EQUIPMENT AND PROCESSES IN LABORATORIES?
Equipment and processes in labs or academic buildings may be affected by fluctuations in hardness, alkalinity, and conductivity over the transition.
To be notified of domestic water quality blend changes in the future, sign up to receive automated emails from our drinking water quality list serve.
Water Quality Background Information:
During normal operations, 100% of the domestic water delivered to the Stanford campus comes from San Francisco Public Utilities Commission (SFPUC). The water is delivered to Stanford University and has already been treated and disinfected with chloramine (the water is also fluoridated and the pH is adjusted for corrosion control). Stanford does not apply additional treatment to the water received from SFPUC.
The source water from SFPUC is typically from the Hetch Hetchy reservoir located in the Sierra Nevada Mountains. Occasionally the source water will shift to local reservoirs during routine maintenance to the conveyance system. During most years, there will be a 30-day shut down of the Hetch Hetchy source in the winter months. More information about this and any other anticipated water quality will be provided through this website and our water quality list serve ahead of planned operational changes.
In addition, sensitive water users on campus should be aware that in the event of an emergency or other operational need, on-campus groundwater wells would be used to supplement or replace the domestic water supply that typically comes from SFPUC. The groundwater from on campus groundwater wells will have significantly different water quality than what is typically received from SFPUC. If you have operations that are sensitive to changes in hardness, dissolved solids, and pH, you should plan for alternative operations during such a change to protect processes, equipment, and/or research. We will send notices through the water quality list serve if groundwater will be introduced into our drinking water distribution system.
Average Water Quality
Below is a summary of average water quality in various treated source water. The reliability, safety, and high quality of drinking water is important to us. If you have any questions, or would like to discuss further, please feel free to contact us.
||SFPUC Treated Surface Water
||SFPUC Treated Surface Water
||Stanford Groundwater Wells
Sunol Valley Water Treatment Plant
|Chlorine residual (total)||mg/L||2.8 (chloramine)||2.8 (chloramine)||0
(could be blended with SFPUC [chloramine] or treated on campus [free chlorine])
|pH||pH||9.6||9.0||7.0 – 7.8|
|Total Dissolved Solids||mg/L||25||195||600|
|Silica||mg/L||3 - 5||3 - 5||25|